(1)The user shall make a plan on the cooling tower site according to the instruction manual or the foundation drawing of the cooling tower provided by the manufacturer.
(2) Cement and sand shall be mixed in a certain proportion, and the embedded steel and steel plate shall be embedded. The upper surface of the embedded steel plate and the surface of the cement foundation shall be on the same level, the upper end of the embedded steel shall be welded with the bottom of the steel plate, and the upper surface of the steel plate shall be welded with the cooling tower foot. The cooling tower shall be installed on a tall building, and the bottom of the embedded steel in the foundation shall be connected with the steel bar on the floor.
(3) The height of the foundation of the cooling tower shall not be lower than the size provided by the manufacturer. The foundation can be raised appropriately according to the requirements of environmental ventilation, multi-set combination, and pipe direction. However, the upper surface of the whole foundation of the cooling tower and the upper surface of the steel plate shall be on the same level, and the error shall not be greater than ±2mm. For the same system, the water level must be equal between different towers to prevent water from flowing between towers due to different heights.
(4) If the cooling tower foundation provided by the customer does not meet the dimension requirements or the steel plate is not welded, the installation engineer can suspend the construction.