Flute Corrugation Angle
Sheet Thickness - Before Forming
Sheet Thickness - After Forming
Max. application temp. (short time) - PVC
Max.operating temp. (short time) - High temp.
The cooling area of the cooling tower filling is effectively used; No deformation; Not broken; System water quality is good; High strength; Low noise and low floating water; Long life; No moss breeding, because of the three-dimensional characteristics of the honeycomb air inlet, so that most of the sunlight can not penetrate the tower body packing surface, so the packing surface is difficult to grow moss.
The filling of the cooling tower is a big hotbed for microbe, and the breeding speed is very fast. After sterilization and algae killing, the micro organism body will accumulate in the system. Moreover, PVC is a degradable plastic, and the combination of PVC monomer and biological corpse produces sludge which is easy to settle on the surface of heat exchanger. Its heat resistance capacity is higher than that of hard scale, and the thermal efficiency of the system is very low. During the annual overhaul, the desilting work is very big, and it is not easy to construct. Sometimes, chemical sedimentation is used, which will cause high cost, great damage to the equipment and shorten the service life of the equipment. Due to the poor cooling effect of the tower and the heat load of the production unit, it is necessary to increase the circulating water volume to take away the heat of the system, the energy consumption of the water pump and fan increases correspondingly, the packing is aging, brittle and deformed seriously, and the packing debris blocks the water pump and heat exchanger seriously, which seriously affects the continuous operation of the production.