The cooling tower float ball, also called the float valve, is designed at the bottom of the pool. When the float ball is lower than the set value, the cooling tower will make up water automatically.
One section of the float ball is fixed on the pool wall of the cooling tower and connected by sliding screws. The float ball can float up and down according to the height of the water surface. The outer end of the float ball is a make-up water interface, which is not connected with the water pipe.
The float ball always floats on the water. When the water surface rises, the float ball also rises. When the float ball rises, the connecting rod also rises. The connecting rod is connected with the valve at the other end. When the cooling tower float ball rises to a certain position, the connecting rod supports the rubber piston pad to close the water source. When the water level drops, the float ball also drops, and the connecting rod drives the piston pad to open.
1. The opening pressure is zero.
2. The small float ball controls the switch of the main valve and has good closing reliability.
3. The circulation capacity is large.
4. High work pressure.
a. The water tank float ball should be installed on the inlet pipe of the water tank or high water tower. The best installation method of the water tank float ball is to horizontally install it on the water pipe, and then put the valve cover upward. Other installation methods of the water tank float ball can also achieve the operation function.
b. Before installing the water tank float ball, the impurities in the water pipe should be thoroughly removed, and then the impurities in the water pipe should be thoroughly cleaned. When installing, the water flow outside the water tank float ball should be marked with arrows, and the installation should follow the direction. When installing the water tank float ball, a gate valve and a filter should be installed, and a gate valve should also be installed after the main valve, so as to facilitate future maintenance.
Float ball are widely used in tap water, water tower, water tank, pool, chemicals, petrochemical, petroleum, paper, mining, power, food, drainage, municipal, mechanical equipment, electronic industry, urban construction and other fields.