Cross flow cooling tower is an equipment that can cool water. The water flows vertically from the top of the tower, and the air flows horizontally through the filler. The air flow is orthogonal to the water flow in the cooling tower.
It is often used in residential areas with strict noise requirements, and it is a cooling circulating tower used more frequently in the air conditioning industry.
|Technical Comparison Between Counter Flow Cooling Tower And Cross flow Cooling Tower|
|Project||Counter Flow Cooling Tower||Cross Flow Cooling Tower|
|Tower Height||Due to the height of the air inlet and the horizontal arrangement of the water eliminator,the total height of the counter flow tower is high and the volume is large.||Because the height of packing is close to the tower height and the water |
eliminator does not occupy the height, the total height of cross flow tower is low and the volume is small.
|Water Distribution System||The counter flow tower adopts the nozzle to distribute water, which has higher requirements on the pressure head and the nozzle is easy to be blocked.||The cross flow tower adopts the water distribution system of gravity falling naturally, so the water dispersion hole is not easy to be blocked, and the water distribution is uniform, which improves the packing performance to the maximum.|
|Overhaul||The whole body of counter flow tower is a closed structure, so it should be shut down during equipment maintenance or routine maintenance.||The cross flow tower body is equipped with an access door, and there is room for maintenance inside the tower, so that the equipment can be overhauled and maintained without shutdown.|
|Wind Resistance||Due to the reverse flow of water and gas in the counter flow tower and the obstruction of water distribution to the air flow, the wind resistance is high and the power consumption of the motor is large.||The cross flow tower is lower than the counter flow tower, and the high air inlet means the high packing, so the air inlet speed is low and the motor power consumption is low.|
|Noise||There is a large distance between the packing of counter flow tower and the lower water tank. After the water falls from the packing, there is a loud noise.||A small part of the lower part of the packing of the cross flow tower is submerged in the water, so that the water flows directly into the lower water tank after passing through the packing surface, and the noise is very low.|
|Water Loss||Because the fan of counter flow tower is located directly above the packing and the distance is close, the water drift is large. In addition, the splash loss of the water in the lower tank is very large, and it is easy to form water mist around the cooling tower, which is easy to cause the reproduction of Legionella.||The cross flow tower fan is located in the center of the cooling tower, and the packing is located on both sides, so the water drift is very small, which is an environmental protection product.|
|Modularization||The unit of counter flow tower is |
supplied with air from all sides, and the air inlet surface is reduced after module combination, which affects the air inlet volume.The power consumption of the motor will increase.
|The cross flow tower is specially designed for modularization, |
with air inlet from both sides of the unit. After the combination of the modules, the air inlet has no change, and the power consumption of the motor remains unchanged.
Energy-saving, low water pressure, small wind resistance, low-speed motor, no dripping noise and wind noise, and convenient maintenance of filler and water distribution system.
According to the shape of the building, the foundation can be built randomly, and multiple cell cooling towers can be started according to the water temperature required.
AUVC cross flow cooling tower casing is made by machine. It makes the casing have a smooth surface and good quantity.
The motor driver we using belt reducer with low noise characteristic. The belt is very stronger, clients no need to replace it frequently. If you choose a cross-flow closed circular cooling tower, we will use a direct drive motor.
The fresh air comes from the cooling tower tow side continuous, the fresh air will take water heat continuously.