The closed cooling tower has been used for a long time, and the location of the closed cooling tower packing is inevitably blocked and damaged, but in order to ensure the actual cooling effect of the closed cooling tower, people often have to replace the new FRP cooling tower packing. So what areas should we pay attention to in advance when replacing the FRP cooling tower filler? Today, master the areas that must be paid attention to in the whole process of dismantling and replacing the enclosed cooling tower packing:
The design scheme of the mold is generally divided into four specifications: 1.0, 1.25, 1.5 and 2.0 meters for different architectural engineering designs. Taking into full account of safety and maintenance, the volume of each module assembly block is not suitable for more than 0.5 cubic meters.
The filling of a closed circuit counter flow cooler should be carried out on the pavement surface. The working temperature on the spot should not be less than 5℃. After installing a group of steel plates, it must be tightened immediately to avoid the plate itself formed by the expansion and contraction of the rubber. It can be placed on the moving part of the road surface on the side of the sticky dry soil, and the cumulative aspect ratio should not exceed two meters. Avoid prolonged sun exposure.
1. The middle of the assembly block should be squeezed tightly and covered. The packing and tower wall, shaft, column and beam should also be extruded and laid, and the large gap should not exceed 20mm. When installing, pay attention to the left and right specificity of the assembled blocks. The top of each layer of the wall should be laid and leveled, and the virtual beam should be cleaned and tidy, and there should be no dirt blocking.
2. When it is necessary to work on the filler during installation, maintenance and other work, be sure to lay the tablet computer to carry out, and it is forbidden to step on it immediately.
3. During the whole process of construction, assembly and installation, it is forbidden to weld the enclosed cooling tower filler, and fire safety measures must be taken.
4. Full-time personnel should be assigned to undertake the installation, and the organization should be strictly inspected anytime and anywhere to ensure the installation quality.
The closed cooling tower packing is generally replaced by PVC material, and the application is simple and clear, and the circle is circled to the circle. The packing interval is 22mm, and the height-width ratio of the packing is 20cm, 25cm, and 30cm. There are two kinds of gray-black and emerald green. If there are other requirements, the closed cooling tower packing can be customized for replacement.